The plant was built in 2016 in an area with an increased earthquake risk and high wind forces (240 km/h), therefore structual calculations and reinforced designs for the steel structures (the storage rack for the stop logs) were required.
Geiger® Fish Protection Technology
Punta Catalina, Dominican Republic
Geiger® fish protection technology and filtration of debris in the water intake of the coal-fired power plant in Punta Catalina, Dominican Republic.
Cooling water intake meets the highest requirements for fish protection and is therefore one of the first plants outside Europe and North America with such a high standard of fish protection solution while filtrating debris.
An electric fish repelling system forms a barrier against swimming fish in front of the water intake structure. Small fish, which cannot be retained by the fish repelling system, are transported upwards by the fish buckets, which are integrated in the travelling band screens and returned to the sea via a separate fish channel and fish return line.
Channel width: 4,4 m
Channel depth: 10,2 m
Flow Rate per channel: 30.000 m³/h sea water
1 Geiger® Fish Repelling System
4 Geiger® Stoplogs with 8 guideways, lifting beams and storage stand
4 Geiger® Cable-Operated Bar Screens
4 Geiger® Centre-Flow Travelling Band Screens with fish return system
Spray water system with submersible pumps
- Optimum protection of larger fish and other aquatic organisms by an upstream electric fish repelling system
- Geiger® Cable-Operated Bar Screens with automated cleaning
- Safe collection and removal of bulky debris
- High load capacity of the cleaner carriage
- Geiger® Centre-Flow Travelling Band Screens (in-to-out-flow) with special screen shape and integrated fish buckets to protect and retract of the smaller fish
- Emptying the fish buckets into a separate fish collecting channel
- Particularly gentle return of fish and biologically valuable substances
- Intensive cleaning of the screen panels with spray water only when descending i.e. after the fish buckets have been emptied